Fire Survival Cables are required where electrical integrity of the cable has to remain intact for at least three hours, so as to activate and maintain crucial functions such as fire fighting, public announcements, smoke extraction systems, sprinklers, emergency lighting, evacuation path lighting systems etc.
The main applications include places where large number of people congregate for short or limited period of time such as shopping malls, cinema theaters, educational institutions, airport terminals, metro rail networks, high rise office buildings etc. These cables also find use in power generation facilities, petrochemical complexes, nuclear power facilities, mines etc. for phased shut down of the plant and to keep critical functions like communication, rescue and evacuation systems functional during a fire.
|Construction||-||Single / Multi - Cores / Pairs / Traids|
|Conductor||-||Solid / Stranded / Flexible - Annealed Bare / Tinned Copper Conductor|
|Fire Barrier||-||Glass Mica Tape|
|Insulation||-||EPR / Silicone Rubber as per IS : 6380|
|Screening||-||Individual and / or overall with following options -|
|-||Al-Mylar / Copper Tape with Tinned Copper Drain Wire or|
|-||Braided with Bare / Tinned / Nickel / Silver Plated Copper|
|Inner Sheath||-||LSOH / ZHFR or equivalent|
|Armouring||-||Galvanized Steel wire helical armouring or wire braiding|
|Outer Sheath||-||LSOH / ZHFR or equivalent|
BS 7211, BS 7846, BS 7629, BS 8434, BS:6387, IEC:60331.
|Temperature Range :||-||-15°C to + 180°C|
|Rated Voltage (Uo/U) :||-||600/1100 V|
|Test Voltage :||-||3.5kV / 5 min|
|Bending Radius (Min) :||-||Upto 8 X cable OD|
|Flammability: IEC 60332-1 & IEC 60332-3|
|Resistance to Fire: BS: 6387, IEC 60331|
|Smoke Emission: IEC 61034 – 2|
|Acid Gas Content: IEC 60754 -1 & 2, BS EN 50267 – 1 & 2|